Shall be able to be opener in one second and kept open constant without hand holding.
It is required to trandmit water 300 Gal in 15 min (75.7 L/min, ie. 20 gal/min)
It is proper to fix 82” (208.3cm)to 96”(248.3cm) from the sround and no other barriers are allowed within 15 around
The flushing water coverage diameter should be more than 20” (50.8cm) when the shower head is 60” (152.4cm) from the application ground
Draw bar of flushing valve
It is proper to keep it 82”(208.3cm) to 96”(248.3cm) from the ground and no other barriers are allowed within 15 cm around
Nozzle of eye wash station
It is required to keep clean and prevent from air pollutant.
Height of the eye wash station outflow nozzle
I is proper to keep it 33” (83.8 cm) to 45” (114.3cm) from the ground and no other barriers are allowed within 15cm around, including the wall
Combination drench shower and eye wash
It is required for the eye wash station to provide at least 20 Gal (11.4L/min) of flushing water within 15 min and hte separate eye wash station is required to provide at least 45 Gal of flushing water within 15 min.
Normal open valve of eye wash station pushing handle
It is required to be able to be opened within one second without hand holding.
Push handle of eye wash station
It is required to be easily identified and operated